Updated: Mar See full version: Eberle instat 2 manual utilizare. Ar- beitstage. Operating instructions for two wire clock thermostat.
|Published (Last):||20 July 2016|
|PDF File Size:||16.86 Mb|
|ePub File Size:||9.32 Mb|
|Price:||Free* [*Free Regsitration Required]|
Libble takes abuse of its services very seriously. We're committed to dealing with such abuse according to the laws in your country of residence.
When you submit a report, we'll investigate it and take the appropriate action. We'll get back to you only if we require additional details or have more information to share. For example, Anti-Semitic content, racist content, or material that could result in a violent physical act. For example, a credit card number, a personal identification number, or an unlisted home address. Note that email addresses and full names are not considered private information. You will receive the manual in your email within minutes.
If you have not received an email, then probably have entered the wrong email address or your mailbox is too full. In addition, it may be that your ISP may have a maximum size for emails to receive.
If you have not received an email with the manual within fifteen minutes, it may be that you have a entered a wrong email address or that your ISP has set a maximum size to receive email that is smaller than the size of the manual. Would you like to receive an email when new answers and questions are posted?
Please enter your email address. Get by email. Function description. T echnical data. Wiring diagrams and examples. Brief operating instructions. This unit must not be opened and installed except by au-. It is mandatory in all work on. In order to classify for protection class II it is necessary to. This separately mounted unit is designed for temperature. This electronic device is created according. EN , it is working according operation principle 1C.
The loads are switched by means of a relay with. The switching condition is indicated by. For relay switching characteristics, see Installation instruc-. For controlling loads, the output can be configured in differ-.
The functions subsequently listed can be combined. Up to 4 transmitters control one output each channels 1…4. One or more actuators can be connected to each. Up to 3 transmitters control one output each channels 1…3. Channel 4 output serves as a common.
The pump is switched off , LED 4. The pump is switched by the break. By parallel connection of the channel 4 outputs, the pump. T o avoid.
Supply slave units via terminal 7, 8 of the master unit, see. This function is always activated, as long as channel 4 is not. Reactivation is possible only via Item 3. This output can, for instance, be used to control the tempera-. Outputs which are. The time switch function is independent.
In frost protec-. In the case of this function, the slaves follow the master. Only slaves in the automatic mode follow the master.
Only one master is possible. It must always be assigned to. In case of. For ex-. Party- and manual mode of the master has. The switching behaviour of all outputs will be.
For heating mode winter time as delivered condition. T o delete all radio links:. Any necessary links must be established new see Item 5. Now, after having pressed the reset button, none. T o determine the distance of the radio link, the following pro-.
Press the channel 2 push-button and reset button simulta-. Release the reset button first, then the channel 2 push-. Channel 2 signal lamp lights up. The signal tone and the. Now, while holding the transmitter in your hand, walk. This is the maximum possible ra-. After a certain period, the transmitter automatically ceases to. Always terminate the radio. Any other channels are not affected by the radio test.
Having pressed the reset button, the programmed channels. The signal lamps provide information about the respective. BR 4, 5: Opening for double-pole insulation of the supply. Insert plug into conduit box. If a direct connection is re-. Before inserting the cables, make a hole in the nipple using a. See diagram on the printed circuit board and Item 8.
In the. The actuators are simply connected to the. Remove bridges BR 4 and BR 5 com. The second voltage is fed via terminals 7, 8 between chan-. V olt free contacts with the required safety clearance can only. A suitable transformer is required for 24 V. Delete all channels before commissioning, see Section 3. On completion of the installation work, a link between the. This must be carried out in the following sequence:.
For function — switching mode —. Set the required switching output of the receiver to. T o do this:. Briefly press the push-button for the desired output. When the transmitter is identified, the signal tone ceases.
For function — pump logic —. As with b 1, however , a transmitter. For function — time switch output —. Set the desired switching output of the receiver and the as-.
A signal. It is not possible to assign one transmitter to several outputs. However , one transmitter can control sever-.
T o establish the ra-. When the push-button of an associated output is pressed:. After releasing the output button, the reset button must be. As a result of this, the signal lamp extinguishes and the signal. After 10 sec.
EBERLE Instat+ 2R
Libble takes abuse of its services very seriously. We're committed to dealing with such abuse according to the laws in your country of residence. When you submit a report, we'll investigate it and take the appropriate action. We'll get back to you only if we require additional details or have more information to share.
EBERLE INSTAT 868-a4
RS Stock No. Product Details. Find alternative products. View Basket.
Mechanical HVAC Thermostat, Eberle INSTAT 2, Changeover 2 A, 8 A
- ALLAMA NIAZ FATEHPURI BOOKS PDF
- CSA S413 PARKING STRUCTURES PDF
- HOW I BRAVED ANU AUNTY PDF
- ALFRED JARRY SUPERMALE PDF
- AL PIE DEL ACANTILADO JULIO RAMON RIBEYRO PDF
- BSBCMM401A MAKE A PRESENTATION PDF
- BAJO EL ESPINO MARITA CONLON MCKENNA PDF
- EL MANUAL DEL PERFECTO ATEO RIUS PDF
- PAULO COELHO CERRANDO CIRCULOS PDF